RE: Change In Enthalpy
This enthalpy change number is based on airflow being correct, the charge being correct, and everything clean and in good working order. It’s a great way to see if a system is working correctly.
Low enthalpy change generally means that there is not enough refrigerant flowing through the coil to meet design temps.
Conversely, a high enthalpy change pretty much always means low airflow.